1000 L/Hr Pure Water Treatment Plants with Reverse Osmosis Membrane
Model No.: 1000 L/hr
Reverse osmosis device is the raw water after fine filter, granular activated carbon filters, compressed activated carbon filter, etc., and then through the pump pressure, use the aperture for 1/10000 microns (1/6000 of 1/6000 of the size of e. Coli, virus) reverse osmosis membrane (RO) membrane, the relatively high concentrations of water into a low concentration of water, at the same time, the industrial pollutants, heavy metals, bacteria, viruses, such as a large number of mixed with the impurities in the water all isolation, so as to achieve the physical and chemical indicators and health standards set by the drinking, output to the qing dynasty to pure water, is the best choice for high quality timely replenish water the human body. Due to the RO reverse osmosis technology in the production of water purity is to master the highest of all the water making technology, almost 100% of cleanliness, so people call the water production machines for reverse osmosis pure water machine.
Application of membrane separation technology, reverse osmosis unit can effectively remove the charged ions in the water, inorganic substance, colloid particles, bacteria and organic matter, etc. High pure water preparation, the best equipment in the desalination of brackish water and wastewater treatment process. Widely used in electronics, medicine, food, textile, chemical, electricity and other fields.
The composition of the Reverse Osmosis System:
Generally includes the original pumps, dosing system, quartz Sand Filter, activated carbon filter, precision filter, etc. Its main function is to reduce the raw water pollution index and residual chlorine and other impurities, to achieve the reverse osmosis water requirements. The equipment configuration of pretreatment system should be based on the raw water of the specific circumstances.
Reverse osmosis unit
Mainly includes the multistage high-pressure pump, reverse osmosis membrane element, membrane shell (pressure vessel), support, etc. Its main function is to remove the impurities in the water, the water meets the requirement.
This is in the case of reverse osmosis can not meet the requirement of the water increases the configuration. Mainly includes the Yin, Yang bed, mixed bed, sterilization, ultrafiltration, EDI and other one or more of these equipment. Post-processing system can increase the reverse osmosis water quality better, make it meet the requirements.
Mainly include cleaning tank, cleaning pump, the precision of filter. When the reverse osmosis system cannot meet the requirements of the pollution of water index, need cleaning restore on reverse osmosis effect.
Electrical control system
This is used to control the normal operation of the reverse osmosis system. Including the instrument panel, control panel, all kinds of electrical protection, electrical control cabinet, etc.
|Type of ions ||Removing efficiency ||Type of ions ||Removing efficiency |
|AI 3+||95-99%||SO 2- 4||90-99%|
|Mn 2+||95-99%||HPO 2- 4||90-99%|
|Ca 2+||92-99%||CO 2- 3||80-95%|
|Mg 2+||92-99%||SiO 2- 3||75-90%|
|K +||75-93%||CF -||85-95%|
|Na +||75-95%||HCO - 3||80-95%|
|NH4 +||70-90%||CI -||80-95%|
|PO 3- 4||90-99%||NO - 3||50-75%|
Product Categories : Reverse Osmosis
Premium Related Products